This fact sheet is for ‘persons conducting a business or undertaking’ (PCBUs) that carry out welding work.
Local exhaust ventilation (LEV) is an engineering control commonly used to control the risks to workers’ health from welding fumes. When designed, used and maintained properly it is an effective control measure.
This fact sheet provides information on some of the health risks associated with welding, LEV systems used for welding and their limitations.
What are welding fumes and what are the health effects?
Welding and hot cutting produce metal and fluxing fumes made up of toxic gases and very fine particles.
Inhaling welding fumes can cause ill health.
Acute (short-term) health effects
Acute bronchitis is short-term inflammation of the large and medium sized airways of the lungs. Symptoms include chest discomfort, wheezing, coughing up mucus and shortness of breath.
Breathing welding fumes can cause a dry tickly throat, cough and tight chest. Ozone gas produced during plasma-arc, metal inert gas (MIG) and tungsten inert gas (TIG) processes can cause blood and fluid to build up in the lungs.
Occupational asthma is commonly associated with exposure to stainless steel fumes. Stainless steel fume contains chromium oxide and nickel oxide which cause asthma. Symptoms include chest tightness, wheezing and shortness of breath.
Metal fume fever is caused by inhaling metal oxides from galvanised welding. Exposure to metal fumes such as zinc, magnesium, copper and copper oxide can cause metal fume fever. The symptoms are similar to the flu and are often worse at the start of the week. Effects usually aren’t long-lasting.
Pneumonitis is inflammation of the lung tissue which can lead to severe and sometimes fatal pneumonia.
Chronic (long-term) health effects
Chronic obstructive pulmonary disease (COPD) includes chronic bronchitis and emphysema. COPD causes permanent lung damage. Symptoms include difficulty breathing, coughing, mucus, and chest tightness. Damage happens gradually over a long period of time so regular health monitoring is important to detect changes.
Cancers in the lung, larynx and urinary tract have been linked to exposure to welding fumes.
Pneumoconiosis is a restrictive lung disease caused by ongoing exposure to fumes from aluminium arc welding.
Note: Research has shown that smoking makes these health effects much worse.
Fatalities have occurred when extremely toxic metals (such as beryllium or cadmium) have been welded or used in welding rods.
Identifying areas of risk
You must start by conducting a risk assessment of the hazards in your workplace before deciding which control measures to use. The assessment could consider:
- Which processes create fumes?
- What substances are in the fumes and the risks associated with them? Detailed information can be found on the Safety Data Sheets for welding electrodes or rods, and shielding gases.
- The type of metal being welded eg galvanised steel, stainless steel, aluminium.
- What welding process are used (TIG, MIG, arc-plasma, brazing or soldering)?
- Are welding surfaces coated or painted with lead based paint, epoxy resins or degreasing agents?
- How concentrated are the fumes?
- The welding temperature.
- Who is exposed to the fumes and for how long?
- Where will the welding be done (inside, outside or confined space)?
Where work activities expose workers to welding fume, WorkSafe recommends PBCUs carry out exposure monitoring to assess the air quality. Exposure monitoring is done by an occupational hygienist or other suitably trained people. They will compare the concentration of contaminants in the air with the relevant workplace exposure standards (WES). They can recommend the right controls for your workplace.
What are the PCBU’s responsibilities?
PCBUs have a duty to ensure, so far as is reasonably practicable, the health and safety of their workers and other workers whose activities they influence or direct. PCBUs must eliminate risks so far as is reasonably practicable and where this is not possible they must minimise them. PCBUs have a duty to monitor the health of workers and the conditions at the workplace to ensure that workers are not injured or made ill by their work.
Reducing the risk from welding fumes
When PCBUs are selecting controls WorkSafe expects, so far as is reasonable practicable, preference to be given to controls that protect multiple at-risk workers at a time. For example local exhaust ventilation (LEV) will protect everyone in the workplace but respiratory protective equipment (RPE) only protects the person wearing it.
PCBUs should apply the most effective controls measures reasonably practicable. In most cases personal protective equipment (PPE) such as RPE shouldn’t be the first or only control considered.
Think about ways to modify the process to eliminate or reduce the amount of hot work or fumes?
- using cold joining techniques such as mechanical fasteners or adhesives
- redesigning the job so thinner gauge material is used
- gas welding rather than full penetration welding
- cleaning welding surfaces to remove any coating that may be toxic such as paint or solvent residue
- using a welding technique that creates less fumes:
- Arc gouging
- Flux core
- Manual metal arc welding (MMA)
- Metal active gas (MAG)
- Flame cutting
- Plasma cutting
- Laser cutting
- Resistance welding
- Submerged arc
Local exhaust ventilation (LEV) as a control measure
LEV is an engineering control that captures hazardous fumes and removes them from the workplace. Most LEV systems will have the following components:
The hood captures the fumes at the source.
To be effective:
- The hood should be positioned as close as possible to the source, ideally less than one hood diameter away.
- The welding area should be enclosed as much as possible to avoid drafts that will blow the fumes away from the hood and/or further into the workplace.
- Ensure the hood is the right design for the process and type of fumes.
- Install an airflow indicator such as a manometer to check that the LEV is working properly.
- The welder must not be positioned between the fumes and the hood.
Capturing hoods are the most common type of LEV hood. The process happens outside the hood. This type of hood requires the LEV system to generate enough air-flow to draw in the fume. There are several types of capturing hood used for welding processes: on-tool, moveable capturing hood fixed capturing hood and extracted workbench.
The ducting system carries the contaminated air away from the work area. Recommended duct velocities are 5 m/s for gases and non-condensing vapours, and 10 m/s for condensing vapours, fumes and smoke.
The air cleaner filters/cleans the air before it’s released (outside, away from inlets).
Fans provide airflow to move the contaminated air from the workplace though the hood and ducting to the exhaust stack.
An exhaust stack or other means of discharging the decontaminated air.
You must make sure that LEV is fit for purpose. The LEV should be designed by an industrial ventilation engineer who has assessed the ventilation needs of your workplace.
The following table provides some examples of the type of extraction that can be used for some common welding processes.
|MIG and MAG welding MMA||
|Oxy-gas welding and brazing||
|Flux-cored arc (FCA) and metalcored arc (MCA)||
|Arc-plasma cutting (fixed equipment)||
|Air carbon arc gouging||
What are the limitations of LEV?
- Selecting and installing LEV can be complicated – you will need to engage a professional to help you select the right system.
- Poor design, installation and maintenance of any one component will reduce the ability of the system to remove the fumes.
- LEV systems require regular checks and maintenance to continue to work properly.
You will need to train workers to complete routine daily checks to see if the LEV is operating as it should. Defects must be reported to supervisors and any faults fixed immediately to ensure effectiveness of this control measure.
- The fans, ducts and hoods will vibrate and are a source of noise.
- Fitting additional hoods can significantly detract from the system’s effectiveness.
- An industrial ventilation engineer should review any changes or additions to the system.
Using LEV and RPE
The LEV system won’t necessarily capture enough of the fumes to keep the workplace safe. LEV engineering controls will usually reduce the level of respiratory protection needed to limit worker exposure. You should conduct further exposure monitoring to determine the type of RPE needed.
Exposure monitoring should be conducted periodically or following any modifications to the process. If the monitoring shows that the current controls are not working effectively PCBUs should seek advice from an occupational health specialist or LEV engineer.
Worker health monitoring is a way to check if workers are getting sick from being exposed to hazards while carrying out their work, it aims to detect early signs of ill-health or disease. Health monitoring can also show if control measures are working effectively.
Where workers are routinely exposed to welding fumes, PCBUs should arrange regular health monitoring for their workers. Monitoring should include a baseline and then annual lung function test and a respiratory questionnaire.
Include results from exposure and health monitoring, including participation levels in the PCBUs health and safety reporting.
The PCBU should follow the recommendations of an occupational health practitioner with experience in health monitoring when determining what type of health monitoring is required.
- Respiratory Equipment – Advice for Employers
- Workplace Exposure Standard and Biological Exposure Indices February 2013
- To find professional occupational health associations: Health and Safety Association of New Zealand(external link)
Key points to remember:
- Conduct a thorough risk assessment.
- Engage a professional to help you select and install the right LEV system.
- Train workers on how to use and check the LEV system.
- Get advice on exposure and health monitoring requirements from a occupational health professional.
 A workplace exposure limit is an upper limit for the acceptable concentration of a hazardous substance in the air in a workplace. They are a guide only and do not guarantee protection from ill health.